This article was first published in the Summer 2012 issue of Spigot News , the Ohio EPA's drinking water program newsletter. Many thanks for allowing us to republish it! You may also be interested in the article Common Source Water Deficiencies . Ohio EPA conducts sanitary surveys at least once every three years at community public water systems (PWS) and once every five years at non-community PWSs. The purpose of a sanitary survey is to evaluate and document the capability of a water system’s source, treatment, storage, distribution, operation and maintenance, and management. Each of these may favorably or adversely impact the ability of the system to reliably produce and distribute water that meets drinking water standards. This article is the second installment in a series of articles to help small water systems identify the most common problems found during a sanitary survey or other investigatory site visit conducted by Ohio EPA staff. The first article focused on source water (well) deficiencies . This article will focus on some of the more common treatment equipment deficiencies which are found during inspections of small water systems. Future articles in this series will cover distribution deficiencies and other topics. Backwash discharge lines: If you have a softener or a pressure filter, you backwash your equipment to clean and replenish the media. The waste that is produced when you backwash discharges into a floor drain or another pipe, which carries the waste to where it will be treated. If the pipe carrying the backwash wastewater from your treatment equipment is too close to, or even inserted into, the drain or pipe that carries the waste to treatment (see Figure 1), you could end up with back-siphonage. This could occur if the pipe carrying the waste to treatment backs up and the wastewater is siphoned back into your drinking water treatment equipment, contaminating your treatment equipment with whatever waste the pipe is carrying. Solution: Ensure there is a sufficient air gap between the backwash waste pipe and the floor drain or the pipe conveying the waste to treatment to prevent backsiphonage (see Figure 2). Softener tanks, cover, and salt: Softener brine tanks should be kept in sanitary condition. The brine solution should be kept free of dirt and insects. Solution: The best way to accomplish this is to completely cover the brine tanks with an appropriately fitting lid. The lid should not be over- or under-sized and should be kept in place on top of the tank. Also, the brine tank should not be overfilled such that the lid does not fit snug on the tank (see Figure 3). All substances, including salt, added to the drinking water in a public water system must conform to standards of the “American National Standards Institute/National Sanitation Foundation” (ANSI/NSF). This is to ensure it is a quality product that will not introduce contaminants into the drinking water. Solution: Ensure the ANSI or NSF symbol can be located on the bags of salt you use or ensure your salt supplier can provide you with documentation from the salt manufacturer that it is ANSI or NSF certified. Cartridge filters: Over time, cartridge filters will become clogged with iron or other minerals from your source water. When clogged, the filters become a breeding ground for bacteria. Solution: Ensure filters are replaced in accordance with the manufacturers’ specifications or even more often, depending on the quality of your source water. General maintenance: Water treatment equipment should be accessible and cleaning solutions and other non-drinking water chemicals and materials should be kept away from the equipment. If treatment equipment is not accessible for Ohio EPA staff to inspect during a sanitary survey, it will not be accessible to the water treatment operator for routine maintenance or during an emergency. Likewise, non-drinking water chemicals stored in close proximity to treatment equipment can be an invitation for a mix-up or, even worse, intentional vandalism (see Figure 4). Solution: Keep clutter and non-drinking water chemicals and equipment away from drinking water treatment equipment. Preferably, these items should be stored in a different room.